Payment & Shipping Terms:
|Item:||House Reverse Osmosis||Stable Rejection::||96~98%|
|Filter:||Ro Water Purifier||Type:||Water Filter Parts|
|Layer:||11~16 Optional To Customer||Color:||Can Be Customize|
Drinking water filter ro membrane manufacturers water treatment equipment 75GPD
Features: the use of ultra- high pressure generated static pressure mercury penetration of water molecules and ionic minerals through a layer of reverse osmosis membrane elements , and dissolved in water most of the heavy metals, organic compounds and bacteria , viruses , etc. are not available through reverse osmosis film is trapped ( reverse osmosis membrane pore long 0.0001um, and the diameter of the virus are generally 0.02-0.4um, common bacteria immediately 0.4-1um).
Semipermeable membrane to remove ions, molecules, and larger particles from drinking water
|Stable Desalination %||96~98%||96~98%||96~98%||96~98%|
Mean Permeable Flow GDP (L/d)
|Active Film Area ft2(m2)||4(0.4)||4.2(0.42)||5.0(0.5)||5.3(0.53)|
|Test Condition||Test Pressure||65pai(0.45Mpa)|
|Test Water Temperature||25℃|
|Test Water Concentration(NaCl)||500ppm|
|Test Water PH||6.5-7.5|
|Recycle Rate %||15|
|Max Operating Temp.||300psi(2.0Mpa)|
|Max. Inlet Water Temp.||45°C|
|Max Water Inlet Silt Density Index (SDI)||5|
|Inlet Water Chlorine Tolerance||<0.1mg/l|
|Inlet Water PH Range, Continuous Operation||3~10|
|Inlet Water PH Range, Short-Term Cleaning||2~11|
|Max. Pressure Drop of Single Membrane||10psi(0.07Mpa)|
After preparing some glycerin, fixed tools, gloves and other protective equipment, please rinse and clean the pre-treatment SDI15<5 Then, check whether there is no sludge, oil or any metal debris in the upstream pipes of Reverse Osmosis. Flush and clean the upstream pipes, the pressure vessels and the high pressure pipes.
Tear off the packing bag and do not move the trademarks and the blue package. Smear a small amount of lubricant at the part of the sealing ring. The end with two small seal rings head into the shell. Screw on the lid and fasten it. Connect the pipe.
1/ Of Uninstalled modules
The modules should be stored in wetting conditions. Please, do not pierce the plastic bags in case of the opening and the checking of the quantity, and store it until its use.
Storage in a ventilated area and protected from direct sunlight with an ambient temperature of 10°C is recommended. The ambient temperature should be under 35°C.
Freezing will damage the performance of the module and its construction, insulation measures should be taken to prevent it.
2/ Of modules installed on a skid
The modules installed should be storaged in a gloom place with a temperature under 35°C, and protected from direct sunlight.
Please, take freezing prevention measures with a temperature under 0°C. Chemicals and flushing should be done regularly after the membrane running sometim
1. Q: Where is your factory, which port for transportation?
A: Our factory located in Xiamen, Welcome to vist our factory. the port is Xiamen port.
2. Q: How can I get some samples?
A: We are glad to provide you the free sample, leave your contact info pls.
3. Q: Can you accept OEM & ODM?
A: Yes, we can accept OEM &ODM
4. Q: What is the delivery time?
A: Within 7 days after receive your payment, accordding to your quantity
5. How to make payment?
A: We accpet T/T,Paypal.Western Union and cash face to face.
6. Q: How can I contact you?
A: Please contact us though below methods, we will reply you within 24 hour.
Contact Person: Kelly Wu